Two AC inputs with integrated transfer switch
The Quattro can be connected to two independent AC sources, for example the public grid and a generator, or two generators. The Quattro will automatically connect to the active source.
Two AC Outputs
The main output has no-break functionality. The Quattro takes over the supply to the connected loads in the event of a grid failure or when shore/generator power is disconnected. This happens so fast (less than 20 milliseconds) that computers and other electronic equipment will continue to operate without disruption.
The second output is live only when AC is available on one of the inputs of the Quattro. Loads that should not discharge the battery, like a water heater for example, can be connected to this output.
Virtually unlimited power thanks to parallel operation
Up to 6 Quattro units can operate in parallel. Six units 48/10000/140, for example, will provide 48kW / 60kVA output power and 840 Amps charging capacity.
Split phase options
Two units can be stacked to provide 120-0-120V, and additional units can be paralleled up to a total of 6 units per phase, to supply up to 30kW / 36kVA of split phase power. Alternatively, a split phase AC source can be obtained by connecting our autotransformer to a ‘European’ inverter programmed to supply 240V / 60Hz.
Three phase capability
Three units can be configured for three phase output. But that’s not all: up to 6 sets of three units can be parallel connected to provide 144kW / 180kVA inverter power and more than 2500A charging capacity.
PowerControl – Dealing with limited generator, shore side or grid power
The Quattro is a very powerful battery charger. It will therefore draw a lot of current from the generator or shore side supply (16A per 5kVA Quattro at 230VAC). A current limit can be set on each AC input. The Quattro will then take account of other AC loads and use whatever is spare for charging, thus preventing the generator or mains supply from being overloaded.
PowerAssist – Boosting shore or generator power
This feature takes the principle of PowerControl to a further dimension allowing the Quattro to supplement the capacity of the alternative source. Where peak power is so often required only for a limited period, the Quattro will make sure that insufficient mains or generator power is immediately compensated for by power from the battery. When the load reduces, the spare power is used to recharge the battery.
Solar energy: AC power available even during a grid failure
The Quattro can be used in off grid as well as grid connected PV and other alternative energy systems. Loss of mains detection software is available.
- In case of a stand-alone application, if settings have to be changed, this can be done in a matter of minutes with a DIP switch setting procedure.
- Parallel and three phase applications can be configured with VE.Bus Quick Configure and VE.Bus System Configurator software.
- Off grid, grid interactive and self-consumption applications, involving grid-tie inverters and/or MPPT Solar Chargers can be configured with Assistants (dedicated software for specific applications).
On-site Monitoring and control
Several options are available: Battery Monitor, Multi Control Panel, Color Control GX or other GX devices, smartphone or tablet (Bluetooth Smart), laptop or computer (USB or RS232).
Remote Monitoring and control
Color Control GX or other GX devices.
Data can be stored and displayed on VRM (Victron Remote Management) website, free of charge.
When connected to the Ethernet, systems with a Color Control GX or other GX device can be accessed and settings can be changed remotely.
|Output AC voltage:||230 VAC|
|Output frequency:||50 Hz|
|Continuous output power at 25°C:||15000 VA|
|Peak power output:||25000 W|
|Input voltage range:||9,5 – 17V / 19 – 33V / 38 – 66V (Inverter)
187 – 265 VAC @ 45-65 Hz (AC Charger)
|Charge current house battery:||200 A (AC Charger)|
|Zero load power:||110 W|
|Battery connection:||Four M8 Bolts|
|230V AC-connection:||M6 Bolts|
|Dimensions (height x width x depth):||572 x 488 x 344 mm|
There are no reviews yet.